On Load Tap Changer (OLTC) Regulating Transformer
This example shows a tap-changing transformer that regulates positive sequence voltage at a 25 kV bus
The Three-Phase Tap-Changing Transformer (Two-Windings) block is used to model an On Load Tap Changer Transformer (OLTC) that regulates positive-sequence voltage at B2 25-kV bus. The reference voltage is set at 1.0 pu.
Observe OLTC reaction for the following 3 events:
1.1 pu over-voltage in 120 kV network at t= 2 sec.
0.95 pu under-voltage in 120 kV network at t= 10 sec.
0.2 sec single-phase fault at B2 bus at t= 20 sec. OLTC does not react because under-voltage duration is lower than specified Delay (0.4 sec)
Note: In order to reduce simulation time, the tap selection time (usually a value between 3 sec and 10 sec) has been shortened to 0.5 sec.